|Place of Origin:||Henan China|
|Model Number:||SIMO Blower 6-06|
|Minimum Order Quantity:||1 Set|
|Packaging Details:||Export Wooden Case Packing, Steel pallet Packing|
|Delivery Time:||15-35 Days|
|Payment Terms:||T/T, L/C, Payment Term Is Negotiable|
|Supply Ability:||500 Sets Per Month|
|Application:||Industrial Ventilation||Feature:||High Performance|
|Power Source:||Three Phase AC Motor||Impeller Support:||SWSI (Single Width, Single Inlet), Impeller Overhung|
Anti Explosion Induced Draft Fan,
Induced Draft Fan Coupling Driving,
ID Fan Coupling Driving
Coupling Driving Industrial Anti-Explosion Induced Draft Fan
Introduction Of Centrifugal Fan
6-06 series centrifugal fan is generally used for gas transportation of granular or powdery materials, and can be widely used to transport air and non-corrosive non-self-igniting, non-viscous substances.
The temperature of the medium generally does not exceed 50°C (max 80°C), the dust and hard particles contained in the medium is not more than 150 mg / m3.
It is suitable for discharging gas containing dust, wood chips and finely divided fibers (If it contains hard particles, a dust removal device must be installed in front of the fan.), it can also be used as a general ventilator for ventilation.
|6-06||8D||1450||1859～2745||11000～26400||15 ~ 22|
|9D||1450||2353～3474||15700～37500||30 ~ 45|
|10D||1450||2905～4289||21500～51500||45 ~ 75|
|11D||960 ~ 1450||1541～5190||22700～68500||22 ~ 110|
|12D||960 ~ 1450||1834～6176||24600～89000||37 ~ 160|
|13D||960 ~ 1450||2152～7248||31200～113000||55 ~ 250|
|14D||960 ~ 1450||2496～8406||39000～141000||75 ~ 400|
|15D||730 ~ 1450||1657～9650||36600～172000||45 ~ 500|
|16D||730 ~ 1450||1885～10980||44300～211000||75 ~ 710|
|17D||730 ~ 960||2128～5433||53200～168000||90 ~ 280|
|18D||730 ~ 960||2386～6091||63100～199000||110 ~ 355|
|19D||730 ~ 960||2658～6787||74200～234000||160 ~ 500|
|20D||730 ~ 960||2946～7520||86700～273000||200 ~ 630|
|21D||580 ~ 960||2050～8290||79500～316000||200 ~ 800|
|22D||580 ~ 960||2250～9099||92200～363000||220 ~ 1000|
|23.5D||580 ~ 960||2567～10380||112000～443000||220 ~ 1400|
|25D||580 ~ 730||6794～6464||134000～406000||355 ~ 800|
|26.5D||480 ~ 730||2236～7633||132000～483000||220 ~ 1120|
|28D||480 ~ 730||2496～8522||156000～569000||315 ~ 1400|
|29.5D||480 ~ 730||2771 ~ 9460||183000～667000||400 ~ 2000|
1. Install centrifugal fans in mines and tunnels to re-enter fresh air and exhaust dirty air to ensure air circulation in the mines and tunnels.Centrifugal fans can help dust discharge, ensure air transparency in mines and tunnels, and ensure the health of workers in mines and tunnels.
2. A centrifugal fan is installed in the cooling tower, which not only plays the role of ventilation and ensures the normal operation of the cooling tower, but also plays a positive role in improving the cooling effect of the cooling tower by the large flow wind generated by the centrifugal fan.
3. Main ventilator in coal mine is an important equipment to ensure normal ventilation in underground mine, which not only affects the production capacity of coal mine, but also is very important to the safety of mining industry.
1.It can output higher outlet pressure and provide more gas flow at the same time, low noise.
2. The fan speed can be flexibly set by matching different belt pulley diameters to make the fan run at the highest efficiency point and reduce energy waste.
3. Motor slide guide can be provided for convenient belt tensioning to reduce energy loss caused by belt slack.
4. The bearing housing is reserved for the installation position of temperature and vibration sensors, which can facilitate the installation of fan operation monitoring device.
5. Use liquid lubricating oil. It is not necessary to open the bearing housing to replace and fill the lubricating oil. The bearing housing is provided with an observation window for easy observation of the quality and stock of the lubricating oil.
6. The bearing housing uses labyrinth mechanical seal, unique anti-leakage design inside, vent hole at the top, and sealing grease at the joint, completely eliminating the possibility of oil leakage in the bearing hosing.
1. What parameters need to be provided when you design the Heat Dissipation Power Plant Blower Fan?
Answers: Air flow, total pressure or static pressure, inlet temperature, local voltage and frequency, Altitude etc.
If there is flammable and explosive gas, or big dust loading in the medium, please also inform the designer.
2. How about your company’s pre-sales service and after-sales service?
Answers: Before our cooperation, we have the professional technical team to help you make the technical solution according to your working condition, to make sure the centrifugal fan efficiency operation.
After sales service, we will offer 12 months’ repairing service, and provide lifelong follow-up services. Besides, our engineers are available for going abroad to offer the repairing service.
3. Does your company have qualifications?
Answers: SIMO Blower has obtained ISO 9001-2008, CE, TUV certifications and so on.