|Place of Origin:||Henan China|
|Model Number:||SIMO Blower 5-06|
|Minimum Order Quantity:||1 Set|
|Packaging Details:||Export Wooden Case Packing, Steel pallet Packing|
|Delivery Time:||15-35 Days|
|Payment Terms:||T/T, L/C, Payment Term Is Negotiable|
|Supply Ability:||500 Sets Per Month|
|Bearing:||SKF/FAG/By Your Demand||Motor:||SIEMENS/ABB/By Your Demand|
|Main Shaft:||High-strength Carbon Structural Steel||System Type:||Single Inlet, Overhang Type|
|Medium:||Clean Air/Dusty Air||Power Source:||Three Phase AC Motor|
3000rpm Centrifugal Ventilation Fans,
Kilns Cooling Centrifugal Ventilation Fans,
3000rpm centrifugal exhaust fan
Kilns Cooling Steam Power Plant Mine Ventilation Centrifugal Blower Fan
The 5-06 series fan can be used in the feeding system of 2-670t/h steam boiler in thermal power plants, it can also meet the requirements of the high-pressure head performance parameters of the fluidized bed furnace.
This series of fans can also be used for dust removal, mine ventilation and general ventilation systems. The blower delivers air, and the induced draft fan delivers flue gas or gas containing foreign particles.
It can be used for more than four years when the concentration of impurities is less than 200 mg/m3.
If it contains a lot of impurities, it also can be used, but it will shorten the service life.
The maximum operating temperature of the induced draft fan must not exceed 250°C.
The performance of the fan is expressed by parameters such as fan flow, full pressure, spindle speed, shaft power and efficiency.
12 pieces of backward aerofoil blades are welded between the Arc cone front plate and the flat shaped rear plate. Because of the use of airfoil blades, the fan is guaranteed to have high efficiency, low noise and high strength. The impeller is corrected by static and dynamic balance, so the operation is stable. Forced draught fan and induced draught fan of the same machine number have same impeller structure.
The casing is a volute welded by ordinary steel plates.
The casing of a single suction fan is made in three different forms: The No. 8 to 12 casing is made into an integral structure and cannot be disassembled; The No. 14 to 16 casing is made into a two open structure; The No. 18~29.5 casing is made into a three open structure.
The induced draft fan and the volute plate are appropriately thickened to prevent wear.
The converging and streamlined air inlet is made into a unitary structure and bolted to the inlet side of the fan.
4. Adjustment door:
A device for regulating the flow of the fan, axially mounted in front of the air inlet. The adjustment range is from 0° (full open) to 90°(fully closed).
5. Transmission parts:
The main shaft of the transmission part is made of high-quality steel, and the 5-51 series of fans are all made of roller bearings.
The bearing housing is available in two forms: No. 8 ~ 16 uses a whole cylindrical bearing housing; No18 ~ 29.5 uses two independent pillow bearing boxes.
The bearing housing is equipped with a thermometer and an oil level indicator (only the induced draft fan). The lubricating oil uses 46# mechanical oil, and the oil quantity is implemented according to the oil level mark. When the No8-16 integral cylindrical bearing housing uses dry oil, the oil retaining plate should be added to the ball side of the bearing housing, and the fixing grooves communicate with each other. The induced draft fan is equipped with a water cooling device, so a water supply pipe must be installed. Water consumption varies with temperature, and is generally considered to be 0.5 to 1 m3/h.
|Series no.||5-06 series||Feature selection|
|Structure||Blade type||Backward, Straight, Aerofoil type|
|Impeller support||SWSI(Single Width, Single Inlet), DWDI(Double Width, Double Inlet), Overhung type|
|Lubrication method||Oil bath lubrication, grease lubrication, lubrication oil station||Can be specified|
|Cooling method||Air cooling, Water cooling, Oil cooling||Can be specified|
|Driven mode||Direct driven, Coupling driven, Belt driven||Can be specified|
|Gas composition||Gas temperature||Normal||Customer request||Customer request||≥250℃||Customer request|
|gas characteristic||Clean gas||Corrosive gas||Particulate dust||High temperature gas||Flammable gas, explosive gas|
|System configuration||Motor brand||Chinese famous brand, ABB, Siemens, WEG etc||Can be specified|
|Impeller||High quality carbon steel||FRP, Stainless steel, Rubber Lining||Wear-resistant layer or wear-resistant liner, ceramic patch||High temperature high quality alloy steel||FRP, Aluminum alloy||Can be specified|
|Air inlet cone||High quality carbon steel||FRP, Stainless steel, Rubber Lining||High quality carbon steel||High quality carbon steel||High quality carbon steel||Can be specified|
|Casing||High quality carbon steel||FRP, Stainless steel, Rubber Lining||High quality carbon steel||High quality carbon steel||High quality carbon steel||Can be specified|
|Air damper||High quality carbon steel||FRP, Stainless steel, Rubber Lining||High quality carbon steel||High quality carbon steel||High quality carbon steel||Can be specified|
|Main shaft||High strength carbon steel, Alloy structural steel||Can be specified|
|Bearing||ZWZ, SKF, FAG, NSK||Can be specified|
|Bearing housing||Cast iron|
|Option parts||System base frame, Protective screening, Silencer, Inlet & Outlet flexible connections, Inlet & Outlet counter flange, Air damper, Electric actuator, Shock absorber, Diaphragm coupling, Fluid coupling, Motor rain cover, Temperature sensor, Vibration sensor, Soft starter, Inverter, Special Electrical Motor, System monitoring Instrument.|
1. What parameters need to be provided when you design the Heat Dissipation Power Plant Blower Fan?
Answers: Air flow, total pressure or static pressure, inlet temperature, local voltage and frequency, Altitude etc.
If there is flammable and explosive gas, or big dust loading in the medium, please also inform the designer.
2. How about your company’s pre-sales service and after-sales service?
Answers: Before our cooperation, we have the professional technical team to help you make the technical solution according to your working condition, to make sure the centrifugal fan efficiency operation.
After sales service, we will offer 12 months’ repairing service, and provide lifelong follow-up services. Besides, our engineers are available for going abroad to offer the repairing service.
3. Does your company have qualifications?
Answers: SIMO Blower has obtained ISO 9001-2008, CE, BV certifications and so on.